We have had temperature and humidity data recorded in the house over the last 4 months as part of a project conducted by Anthony Mach, a passive house designer and Building Science research student at Algonquin College. The preliminary data is now available, courtesy of Anthony. What we have here is essentially the raw temperature and humidity records in two locations: one in the middle of the open-plan downstairs space (1st Floor), and the other upstairs on the landing (2nd Floor). There is a lot of analysis to be done with this data combined with other data on external temperatures, energy use and so on.
A few things to note when looking at these charts:
- We were only half-moved in for most of November – we started using the kitchen sometime in the second week.
- When we moved in (around the 21st November), the HRV (which actually turned out to have an ERV core – for more on the differences, see here) had still not been properly balanced and we were still only using the system on its lowest setting.
- After the HRV had been balanced properly on the 4th December, we started using it on the middle setting, with boosts after baths and during cooking.
- We only had the 2kW Thermolec heating element, that works with the HRV, installed on December 14th. Up until that point we had only been using a single 1kW space heater. If it was cloudy in the morning after this point we used both, but if it was sunny we didn’t need the later.
- However, that installation coincided with a serious cold spell where external temperatures dropped to -25ºC or lower.
- We were away from the 20th to the 30th of December, and had the HRV just ticking over, which means that the house would have had almost no internal heating. You can see the drop, but what’s remarkable is that the place still never got below 13ºC.
- Once everything was back to normal and functioning properly, from early January, the temperatures in the house were generally between 17ºC (average night-time low) and 19ºC (average day time high) upstairs, with the extremes being 15.5ºC and 21ºC; and 18ºC (average night-time low) and 20.5ºC (average day time high) upstairs, with extremes of 16.5ºC and 22ºC. The difference is probably explained by a combination of the use of the extra heating downstairs, the passive solar effect from the larger windows, and generally that there is more activity downstairs for more of the time.
- The humidity has generally been where you’d want it, between 40 and 50%, gradually drying out as winter goes on. Our HRV having an ERV core helps in stopping the place getting too dry.